Waste Water Treatment Plants india, Drinking Water Treatment Plant, Potable Water Treatment Plant, Demineralisation treatment plants india, Condensate Polishing Plant India, Sewage treatment Plants india, Ash handling Plants, Pre treatment Plant india, Effluent Recycling treatment Plants, Boiler feed water treatment, Reverse osmosis Plant, Ultrafiltration Plant India, Power plant water treatment india, Pneumatic Conveying system, Bottom ash handling system, Slurry disposal system, Water supply schemes, Boiler condensate treatment Plants, Mixed bed resin treatment plants, Ion exchange plants, Packed bed demineralisers, Condensate treatment - External Regeneration, External regeneration condensate treatment plants, Municipal Drinking Water treatment India, Softening Water Plants India, Mixed Bed Polishers, Membrane Water Treatment Systems, Desalination Plants, Plant Water Treatment System, Sludge Handling System
Industrial | Pre Treatment Plant
The nature and concentration of impurities and objectionable constituents of water determine the methods to be employed for the treatment of water. Different techniques are used for removal of mechanical impurities, Clayey turbidities, Colloidal, dissolved impurities, organic matter, detergents, polycyclic aromatics, coloring substances, oils and aliphatic hydrocarbons etc. which impart taste or odour, polyvalent heavy-metal compounds, germs and bacteria
Typical Scheme For Pre Treatment Plants
Raw water is pumped to an Aerator, which oxidizes soluble iron in the Raw Water from Ferrous to Ferric State.
Water flows to the Stilling Chamber to break the turbulence.
Water is then taken into the Flash Mixer for intimate mixing of chemicals with the raw water.
The raw water is dosed with Alum, Lime and Polyelectrolyte to coagulate and flocculate the suspended / colloidal matter and form floc of higher nuclei thereby enhancing the efficiency of sedimentation.
Chemically dosed raw water is then fed into the clarifier unit wherein flocculation and clarification of raw water takes place.
The sludge generated in the clarifier is bled via Telescopic Bleeds to an underground Sludge Pit. The sludge collected from the plant is finally pumped out.
Clarified water is collected in the launder of the clarifier located on the top periphery from where it flows to the clarified water reservoir.
Water collected in clarified water reservoir is then pumped to various consuming points.